Recently, our customer from Uzbekistan, purchased our horticultural purification reverse osmosis water treatment plant.Reverse osmosis water treatment plants can be used in a variety of applications and whenever you need water, then you probably need it.
When reverse osmosis membrane elements are used, the RO feed water should be dechlorinated in order to prevent the membrane from being oxidized. RO membranes have a degree of resistance to chlorine until a significant drop in desalination occurs, which is approximately 200-1000 hours of exposure to
Industrial boilers currently commonly used sodium ion exchange method for water treatment, there is a high rate of boiler discharge, heat loss and other disadvantages. With the development of water treatment technology, the use of reverse osmosis membrane water treatment technology, can effectiv
What is reverse osmosis membrane heavy contaminationAs a means of deep filtration, reverse osmosis membrane elements will inevitably have colloids, microorganisms, impurity particles and insoluble salts precipitating on their surface, so reverse osmosis units used in a variety of fields will eventua
Reverse Osmosis Membrane Technology and PrinciplesIntroduction.Membrane separation technology refers to the technology of selective separation of a mixture of molecules of different particle sizes at the molecular level when passing through a semi-permeable membrane, also known as a separation membr
1.How often should the reverse osmosis system be cleaned? In general, when the standardized flux drops by 10-15%, or the system desalination rate drops by 10-15%, or the operating pressure and the pressure difference between sections increase by 10-15%, the RO system should be cleaned. The c
How often should the reverse osmosis system be cleaned?In general, when the standardized flux decreases by 10-15%, or the system desalination rate decreases by 10-15%, or the operating pressure and differential pressure between segments increases by 10-15%, the RO system should be cleaned. Cleaning